The outer heath is of PVC compound confirming to the requiremnets of type 6 compund of IS:58311970.
The colour of outer sheath is genereally Black.
CABLE CODE:
The following code is used for easy identification of the cables.
META PLAST 1.1KV SINGLE CORE, ALUMINIUM CONDUCTOR, PVC INSULATED
UNARMOURED & PVC SHEATHED CABLES AS PER IS:1554 (PART I) AMENDED UPTO DATE
Nominal cross sectional area 
Nominal thickness of Insualtion 
Nominal thickness of Outer Sheath 
Approx overall diameter 
Approx weight of cable 
Max. Dc conductor resistance at 200 C 
CURRENT RATINGS 
Direct in Ground 
In Duct 
In Air 
2 cables Amps 
3 cables Amps 
2 cables Amps 
3 cables Amps 
2 cables Amps 
3 cables Amps 
Sq.mm 
mm 
mm 
mm 
kg / km 
Ohm / km 
1 x 1.5 
1.1 
1.8 
7.4 
63 
19.7 
21 
17 
19 
17 
18 
15 
1 x 2.5* 
1.2 
1.8 
8.0 
74 
11.8 
28 
24 
25 
24 
25 
21 
1 x 4* 
1.3 
1.8 
8.7 
88 
7.39 
36 
31 
33 
30 
32 
27 
1 x 6* 
1.3 
1.8 
9.2 
101 
4.91 
44 
39 
42 
37 
41 
35 
1 x 10* 
1.3 
1.8 
10.0 
122 
2.94 
54 
51 
56 
51 
56 
47 
1 x 16 
1.3 
1.8 
11.5 
161 
1.87 
75 
66 
71 
65 
72 
64 
1 x 25 
1.5 
1.8 
12.9 
209 
1.18 
97 
86 
93 
84 
99 
84 
1 x 35 
1.5 
1.8 
14.0 
251 
0.851 
120 
100 
110 
100 
120 
105 
1 x 50 
1.5 
1.8 
15.2 
301 
0.628 
145 
120 
130 
115 
150 
130 
1 x 70 
1.5 
1.8 
17.0 
386 
0.435 
170 
140 
155 
135 
185 
155 
1 x 95 
1.6 
2.0 
19.4 
510 
0.313 
205 
175 
180 
155 
215 
190 
1 x 120 
1.6 
2.0 
20.9 
601 
0.248 
230 
195 
200 
170 
240 
220 
1 x 150 
1.8 
2.0 
22.8 
722 
0.202 
265 
220 
220 
190 
270 
250 
1 x 185 
2.0 
2.0 
25.0 
871 
0.161 
300 
240 
240 
210 
305 
290 
1 x 240 
2.2 
2.0 
27.9 
1098 
0.122 
335 
270 
270 
225 
350 
335 
* If required, cables can be made with stranded conductor also. *Not covered in IS : 1554 (Part 1) 1976
META PLAST 1.1 KV TWIN CORE, ALUMINIUM CONDUCTOR, PVC INSULATED INNER SHEATHED
UNARMOURED & PVC SHEATHED CABLES AS PER IS: 1554 (PART I) AMENDED UPTO DATE
Nominal cross sectional area 
Nominal thickness of Insualtion 
Minium thickness of Inner Sheath 
Normal thickness Outer Sheath 
Approx overallt of cable 
Approx weight of cable 
Max. Dc conductor resistance at 200 C 
CURRENT RATINGS 
Direct in Ground 
In Duct 
In Air 
Amps 
Amps 
Amps 
Sq.mm 
Mm 
Mm 
Mm 
Mm 
kg / km 
Ohm / km 
2 x 1.5 
0.8 
0.3 
1.8 
10.4 
135 
20.0 
18 
16 
16 
2 x 2.5* 
0.9 
0.3 
1.8 
11.6 
194 
12.0 
25 
21 
21 
2 x 4* 
1.0 
0.3 
1.8 
13.0 
247 
7.54 
32 
27 
27 
2 x 6* 
1.0 
0.3 
1.8 
14.0 
258 
5.01 
40 
34 
35 
2 x 10* 
1.0 
0.3 
1.8 
15.6 
351 
3.00 
55 
45 
47 
2 x 16 
1.0 
0.3 
1.8 
16.5 
364 
1.91 
70 
58 
59 
2 x 25 
1.2 
0.3 
2.0 
19.4 
480 
1.20 
90 
76 
78 
2 x 35 
1.2 
0.3 
2.0 
21.0 
600 
0.868 
110 
92 
99 
2 x 50 
1.4 
0.3 
2.0 
23.7 
750 
0.641 
135 
115 
125 
2 x 70 
1.4 
0.3 
2.0 
26.3 
900 
0.443 
160 
140 
150 
* If required, cables can be made with stranded conductor also. *Not covered in IS : 1554 (Part 1) 1976
META PLAST 1.1 KV THREE CORE, ALUMINIUM CONDUCTOR, PVC INSULATED INNER SHEATHED UNARMOURED & PVC
SHEATHED CABLES AS PER IS:1554 (PART I) AMENDED UPTO DATE
Nominal cross sectional area 
Nominal thickness of Insualtion 
Minium thickness of Inner Sheath 
Normal thickness Outer Sheath 
Approx overallt of cable 
Approx weight of cable 
Max. Dc conductor resistance at 200 C 
CURRENT RATINGS 
Direct in Ground 
In Duct 
In Air 
Amps 
Amps 
Amps 
Sq.mm 
Mm 
Mm 
Mm 
Mm 
kg / km 
Ohm / km 
3 x 1.5 
0.8 
0.3 
1.8 
10.9 
160 
20.0 
16 
14 
13 
3 x 2.5* 
0.9 
0.3 
1.8 
12.2 
221 
12.0 
21 
18 
18 
3 x 4* 
1.0 
0.3 
1.8 
13.7 
242 
7.54 
28 
23 
23 
3 x 6* 
1.0 
0.3 
1.8 
14.8 
320 
5.01 
35 
30 
30 
3 x 10* 
1.0 
0.3 
1.8 
16.5 
366 
3.00 
46 
39 
40 
3 x 16 
1.0 
0.3 
1.8 
17.8 
436 
1.91 
60 
50 
51 
3 x 25 
1.2 
0.3 
2.0 
21.2 
630 
1.20 
76 
63 
70 
3 x 35 
1.2 
0.3 
2.0 
23.1 
706 
0.868 
92 
77 
86 
3 x 50 
1.4 
0.3 
2.0 
26.1 
903 
0.641 
110 
95 
105 
3 x 70 
1.4 
0.3 
2.2 
29.7 
1200 
0.443 
135 
115 
130 
* If required, cables can be made with stranded conductor also. *Not covered in IS : 1554 (Part 1) 1976
META PLAST 1.1 KV 31/2 CORE, ALUMINIUM CONDUCTOR, PVC INSULATED INNER SHEATHED UNARMOURED & PVC SHEATHED
CABLES CONFORMING TO IS :1554 (PART I) AMENDED UPTO DATE
Nominal cross sectional area 
Nominal thickness of insulation 
Minimum thickness of inner sheath 
Minimum thickness of Outer sheath 
Approx overall diameter 
Approx weight of cable 
Max. DC conductor resistance at 20°C 
CURRENT RATINGS 
Sq.mm 
Neutral
Sq.mm 
Main mm 
Neutral
Smm 
Mm 
Mm 
Mm 
Kg/ Km 
Main Ohm / km 
Neutral Ohm / km 
Direct in Ground Amps 
In Ducts Amps 
In Air Amps 
31/2 x 35 
16 
1.2 
1.0 
0.3 
2.0 
23.9 
702 
1.20 
1.91 
76 
63 
70 
31/2 x 25 
16 
1.2 
1.0 
0.3 
2.0 
26.2 
800 
0.868 
1.91 
92 
77 
86 
31/2 x 50 
25 
1.4 
1.2 
0.3 
2.2 
29.5 
1027 
0.641 
1.20 
110 
95 
105 
31/2 x 70 
35 
1.4 
1.2 
0.3 
2.2 
33.5 
1550 
0.443 
0.868 
135 
115 
130 
META PLAST 1.1 KV FOUR CORE, ALUMINIUM CONDUCTOR, PVC INSULATED INNER SHEATHED UNARMOURED & PVC SHEATHED
CABLES AS PER IS :1554 (PART I) AMENDED UPTO DATE
Nominal cross sectional area 
Nominal thickness of Insualtion 
Minium thickness of Inner Sheath 
Normal thickness Outer Sheath 
Approx overallt of cable 
Approx weight of cable 
Max. Dc conductor resistance at 200 C 
CURRENT RATINGS 
Direct in Ground 
In Duct 
In Air 
Amps 
Amps 
Amps 
Sq.mm 
Mm 
Mm 
Mm 
Mm 
kg / km 
Ohm / km 
4 x 1.5 
0.8 
0.3 
1.8 
11.7 
180 
20.0 
16 
14 
13 
4 x 2.5* 
0.9 
0.3 
1.8 
13.1 
225 
12.0 
21 
18 
18 
4 x 4* 
1.0 
0.3 
1.8 
14.8 
269 
7.54 
28 
23 
23 
4 x 6* 
1.0 
0.3 
1.8 
16.0 
316 
5.01 
35 
30 
30 
4 x 10* 
1.0 
0.3 
1.8 
17.9 
411 
3.00 
46 
39 
40 
4 x 16 
1.0 
0.3 
2.0 
20.3 
532 
1.91 
60 
50 
51 
4 x 25 
1.2 
0.3 
2.0 
23.9 
719 
1.20 
76 
63 
70 
4 x 35 
1.2 
0.3 
2.0 
26.0 
897 
0.868 
92 
77 
86 
4 x 50 
1.4 
0.3 
2.2 
30.1 
1189 
0.641 
110 
95 
105 
4 x 70 
1.4 
0.4 
2.2 
33.9 
1548 
0.443 
135 
115 
130 
* If required, cables can be made with stranded conductor also. *Not covered in IS : 1554 (Part 1) 1976
META PLAST 1.1KV TWIN CORE, ALUMINIUM CONDUCTOR, PVC INSULATED INNER SHEATHER ARMOURED & PVC SHEATHED
CABLES AS PER IS : 1554 (PART I) AMENDED UPTO DATE
Nominal cross sectional area 
Nominal thickness of Insulation 
Minimum thickness of Inner sheath 
ARMOUR 
Nominal thickness of Outer sheath 
Approx overall diameter 
Approx weight of cable 
Max Dc conductor resistance at 20°C 
CURRENT RATINGS 

Galv.Round Steel Wire Normal diameter 
Galv.Flat Steel Strip Normal thickness 

Direct in Ground 
In Ducts 
In Air 
Sq.mm 
mm 
mm 
mm 
mm 
mm 
mm 
Kg/km 
Ohm/km 
Amps 
Amps 
Amps 
2 x 1.5 
0.8 
0.3 
1.4 
 
1.8 
13.6 
410 
20.0 
18 
16 
16 
2 x 2.5* 
0.9 
0.3 
1.4 
 
1.8 
14.8 
472 
12.0 
25 
21 
21 
2 x 4* 
1.0 
0.3 
1.4 
 
1.8 
16.2 
568 
7.54 
32 
27 
27 
2 x 6* 
1.0 
0.3 
1.4 
 
1.8 
17.2 
632 
5.01 
40 
34 
35 
2 x 10* 
1.0 
0.3 
1.4 
 
1.8 
18.3 
750 
3.00 
55 
45 
47 
2 x 16 
1.0 
0.3 
 
0.8 
2.0 
19.7 
770 
1.91 
70 
58 
59 
2 x 25 
1.2 
0.3 
 
0.8 
2.0 
21.2 
800 
1.20 
90 
76 
78 
2 x 35 
1.2 
0.3 
 
0.8 
2.0 
22.9 
920 
0.868 
110 
92 
99 
2 x 50 
1.4 
0.3 
 
0.8 
2.0 
25.6 
1042 
0.641 
135 
115 
125 
* If required, cables can be made with stranded conductor also. *Not covered in IS : 1554 (Part 1) 1976
META PLAST 1.1KV THREE CORE, ALUMINIUM CONDUCTOR, PVC INSULATED INNER SHEATHER ARMOURED & PVC
SHEATHED CABLES AS PER IS : 1554 (PART I) AMENDED UPTO DATE
Nominal cross sectional area 
Nominal thickness of Insulation 
Minimum thickness of Inner sheath 
ARMOUR 
Nominal thickness of Outer sheath 
Approx overall diameter 
Approx weight of cable 
Max Dc conductor resistance at 20°C 
CURRENT RATINGS 
Galv.Round Steel Wire Normal diameter 
Galv.Flat Steel Strip Normal thickness 
Direct in Ground 
In Ducts 
In Air 
Sq.mm 
mm 
mm 
mm 
mm 
mm 
mm 
Kg/km 
Ohm/km 
Amps 
Amps 
Amps 
3 x 1.5 
0.8 
0.3 
1.4 
 
1.8 
14.1 
440 
20.0 
16 
14 
13 
3 x 2.5* 
0.9 
0.3 
1.4 
 
1.8 
15.4 
520 
12.0 
21 
18 
18 
3 x 4* 
1.0 
0.3 
1.4 
 
1.8 
16.9 
613 
7.54 
28 
23 
23 
3 x 6* 
1.0 
0.3 
1.4 
 
1.8 
18.0 
680 
5.01 
35 
30 
30 
3 x 10* 
1.0 
0.3 
 
0.8 
2.0 
19.4 
720 
3.00 
46 
39 
40 
3 x 16 
1.0 
0.3 
 
0.8 
2.0 
20.1 
766 
1.91 
60 
50 
51 
3 x 25 
1.2 
0.3 
 
0.8 
2.0 
23.1 
920 
1.20 
76 
63 
70 
3 x 35 
1.2 
0.3 
 
0.8 
2.0 
25.0 
1047 
0.868 
92 
77 
86 
3 x 50 
1.4 
0.3 
 
0.8 
2.0 
28.0 
1249 
0.641 
110 
95 
105 
* If required, cables can be made with stranded conductor also. *Not covered in IS : 1554 (Part 1) 1976
META PLAST 1.1KV 31/2 CORE, ALUMINIUM CONDUCTOR, PVC INSULATED INNER SHEATHER ARMOURED & PVC
SHEATHED CABLES AS PER IS : 1554 (PART I) AMENDED UPTO DATE
Nominal cross sectional area 
Nominal thickness of Insulation 
Minimum thickness of Inner sheath 
ARMOUR 
Nominal thickness of Outer sheath 
Approx diameter 
Approx weight of cable 
Max Dc conductor resistance at 20°C 
CURRENT RATINGS 

Galv.Flat Steel Strip 

Direct in Ground 
In Ducts 
In Air 

Main Sq.mm 
Neutral Sq.mm 
Main Sq.mm 
Neutral Sq.mm 
Mm 
Mm 
Mm 
Mm 
Kg/km 
Main
Ohm/km 
Neutral
Ohm/km 
Amps 
Amps 
Amps 
31/2 x 25 
16 
1.2 
1.0 
0.3 
0.8 
2.0 
25.8 
1048 
1.20 
1.91 
76 
63 
70 
31/2 x 35 
16 
1.2 
1.0 
0.3 
0.8 
2.0 
28.1 
1221 
0.868 
1.91 
92 
77 
86 
31/2 x 50 
25 
1.4 
1.2 
0.3 
0.8 
2.2 
31.4 
1529 
0.641 
1.20 
100 
95 
105 
METAPLAST 1.1 KV FOUR CORE, ALUMINIUM CONDUCTOR, PVC INSULATED INNER SHEATHED ARMOURED PVC
SHEATHED CABLES AS PER IS :1554 (PART 1) AMENDED UPTO DATE
* If required, cables can be made with stranded conductor also. *Not covered in IS : 1554 (Part 1) 1976
METAPLAST 1.1 KV ANNEALED HIGH CONDUCTIVITY SOLID COPPER CONDUCTOR 1.5 Sq. mm. PVCINSULATED INNER SHEED, ARMOURED / UNARMOURED &
PVC SHEATHED CONTROL CABLES AS PER IS :1554 (PART 1) AMENDED UPTO DATE